## Pump performance curves

Pump performance curves are important drawings produced by the pump manufacturer. Pump performance curves are primarily used to predict the variation of the differential head across the pump, as the flow is changed. But in addition variation of efficiency, power, NPSH required etc, as the flow is changed, can also be represented on the pump performance curves by the manufacturer.

It is important to be able to read and understand the pump curves for selection, testing, operation and maintenance of pumps.

Typically a pump performance curve will carry information about the following points.

## Variation of differential head Vs flow

This is the primary information reported in the pump performance curves and very important information regarding most of the pump calculations related to differential pressure across the pump. As shown in the sample performance curves, usually 3 curves of differential head Vs. volumetric flow are reported.

Differential head Δh is related to differential pressure ΔP by the equation, ΔP = ρgΔh.

- Curve of differential head for
**Rated Impeller Diameter**represents the variation of differential head with volumetric flow for the impeller with rated diameter which will actually be provided with the pump. - Variation of differential head with volumetric flow for
**Maximum Impeller Diameter**is plotted for the impeller with the maximum diameter that can be accommodated within the pump. This impeller can be used in case flow through the pump is increased or if more differential head is required in the future, with the same pump. - Variation of differential head with volumetric flow for
**Minimum Impeller Diameter**is plotted for the impeller with minimum possible diameter. If the flow or differential head requirement is reduced in future, this impeller can be used with lower power consumption.

Although the 3 curves are plotted for a wide range of volumetric flow rates, the actual operation is to be limited within the **Maximum and Minimum allowable flow rates** as indicated in the sample pump performance curve. Values of the maximum and minimum flow limits are given by the pump manufacturer.

The point on differential head axis (Y-axis) where each of these 3 curves terminates, represents the **shut-off differential head** for that particular impeller diameter. For normal intended operation, the shut-off differential head for rated impeller diameter is important.

It should be note that the pump curves for differential head Vs. volumetric flow rate are plotted for a particular liquid density. If in the future the process liquid or even just liquid density is changed, that effect has to be considered to finally determine the differential pressure. In such as case, revised volumetric flow should be calculated and located on the pump curve and corresponding differential head should be then determined from the curve for the appropriate impeller diameter. This differential head should then be used along with the changed liquid density to determine the differential pressure across the pump.

## Pump Efficiency

As indicated in the sample pump performance curve above, the plot of pump efficiency against volumetric flow rate is also commonly reported on the pump performance curves. When the theoretical pumping power requirement is divided by this efficiency for the corresponding flow, the result is pump shaft power requirement. For more information on pump power calculations using efficiency, refer to EnggCyclopedia's solved sample problem. The calculated pump shaft power has to be provided by an electric motor.

The efficiency curve typically has a maximum within the allowable operating range. This maximum is also known as the** Best Efficiency Point (BEP)** as indicated in the sample curves. The normal operation should be preferably done close this best efficiency point for minimum power requirements.

Sometimes a plot of **Pump Shaft Power requirement** is also done against the volumetric flow rate on the performance curves. This curve readily gives the value of power requirement for a particular flow rate.

## NPSHR (Net Positive Suction Head Required)

Every pump requires certain Net Positive Suction Head (NPSH), for safe and smooth operation and to avoid cavitation in the pumps. The pump manufacturer provides these values by plotting them against the volumetric flow. As seen from the sample performance curves, NPSH requirement increases for increase in volumetric flow. When designing a pump system and positioning the pump, it must always be ensured that NPSH Available is higher than the NPSH requirement as per pump curves. For details about calculation NPSH Available, refer to EnggCyclopedia's solved sample problem.

## Examples of pump curves

Different pump manufacturers have different formats for their pump curves diagram. Therefore, sometimes the pump curves can look a bit confusing at first. Sometimes there will be multiple lines on a single chart and you may not be sure about the meaning of each line. In such cases, always look for the label of each curve.

For example consider the following pump curve chart.

There are multiple curves here, on a single chart. But the good thing is that they are properly labeled. The green curve clearly represents the variation of "head Vs flowrate". The head is maximum at zero flow and drops down as the flow is increased. Notably, the "head vs. flowrate" curve is only plotted for a single impeller size.

Further, there is another U shaped curve of brown color. This represents the variation of pump efficiency against the flowrate. Peak point on the efficiency curve is clearly marked on the chart as the - best efficiency point (BEP).

Finally, there is an orange color curve at the bottom indicating the required NPSH (NPSHr) for different flowrates. As the flowrate increases, so do the frictional losses. Hence at NPSHr goes up with increasing flowrate.

But not all pump curves are so nicely labeled. For example, consider this pump curve chart.

In this case there are multiple curves on the chart and they are not very clearly labeled. But if you have understood different types of pump curves by now, you can easily guess that the multiple parallel curves at the top, represent "head Vs flow". Each of those curves are labeled with different pump impeller diameters in inches - ranging from 7" to 9.5". Clearly, the differential head increases as you use larger pump impellers.

Then you can also see an upward trending curve at the bottom of the chart. That is the "NPSHr vs flowrate" curve.

Notably, there is no separate U shaped efficiency curve on this chart. But, you can still see few contours running across the "head Vs flow" plots. These are the efficiency contours plotted across the "head Vs flow". Each contour is labeled with % efficiency. You can see the maximum value to be close to 80%, at the center of all contours. That center is the best efficiency point (BEP) for this pump curve chart.